|Fire Rating||Application||Max CV Area||Max CV W||Max CV H||Stops|
|20-90 min.||Sidelites Windows Transoms||3,143 in²||75"||75"||5/8"|
|20-90 min.||Doors (Non-Temp.Rise)||2,736 in²||36"||75"||5/8"|
|up to 180 min.||Doors (Temp. Rise)||100 in²||12"||33"||1/2"|
PYRAN® Platinum L by SAFTI FIRST is listed and labeled by Intertek/Warnock-Hersey Inc. and Underwriters Laboratories, nationally recognized testing laboratories approved by OSHA.
All ceramic products do not meet ASTM E119 or NFPA 251 and should not be used in such applications.
UL 9, UL 10B, UL 10C, NFPA 80, NFPA 252, NFPA 257, ASTM E2074, ASTM E2010-01, CPSC 16 CFR 1201 Cat. I and II, ULC CAN4-S104, ULC CAN4-S106.
See how filmed wire, filmed ceramic, laminated ceramic and SAFTI FIRST's SuperClear® 45-HS-LI performs in the same CPSC Cat. II 400 ft. lbs. impact test. To view all our videos, click here